Home

On psychrometric chart, wet bulb temperature lines are

Psychrometric chart illustrates enthalpy scale (line with a slope), dry-bulb temperature scale (horizontal line), and specific humidity scale (vertical line). Wet-bulb temperature scale is indicated on the saturated curve (relative humidity %) Lines of constant wet bulb temperatures run diagonally from the upper left to the lower right in the Psychrometric chart. Dew Point Temperature Dew point temperature is the temperature at which the mixture of air and water vapor is saturated Identify a point on psychrometric chart when wet bulb temperature and dry bulb temperature are known When wet bulb temperature and dry bulb temperature are given, your first step is drawing correct lines of wet bulb temperature and dry bulb temperature. Then these two lines will meet at one point Psychrometric chart illustrates enthalpy scale (line with a slope), dry-bulb temperature scale (horizontal line), and specific humidity scale (vertical line). Wet-bulb temperature scale is indicated on the saturated curve (relative humidity 100%) Boundaries of the psychrometric chart are a dry-bulb temperature scale on the horizontal axis, a humidity ratio (moisture content) scale on the vertical axis, and an upper curved boundary which represents saturated air or 100-percent moisture holding capacity

How to find wet bulb temperature using psychrometric char

• The wet bulb temperature is always lower than the dry bulb temperature but will be identical with 100% relative humidity (the air is at the saturation line). Combining the dry bulb and wet bulb temperature in a psychrometric diagram or Mollier chart, gives the state of the humid air
• On the psych chart: Wet bulb temperature lines run diagonally downward from the saturation curve toward the right. Dew point temperature. This one's similar to wet bulb temperature but in the opposite direction. Wet bulb is the temperature of evaporation. Dew point is the temperature of condensation
• A. Wet bulb temperature=dry bulb temperature B. Wet bulb temperature=dew point temperature C. Saturation temperature=dew point temperature D. All 'A', 'B' & 'C' Related Mcqs: About _________________ ton of coke is required in a cupola to produce one ton of casting ? A. 0.03 B. 0.3 C. 0.8 D. 1.5... The capacity of a spring The dew point temperature lines on psychrometric charts.
• The curved lines on a psychrometric chart indicates a) Dry bulb temperature b) Wet bulb temperature c) Dew point temperature d) Relative humidit

Pyschrometric chart - Chemepedi

You can also read the web-bulb temperature from a Psychrometric chart. From the current point, draw a line parallel to the lines of constant wet-bulb temperature, until you reach the 100% relative humidity line, and then read the temperature. This is illustrates by the green line on the chart below. > Use the psychrometric chart to determine the specific humidity ω [ 18 gm-moisture/kg-air ], the enthalpy h [ 78 kJ/kg-air ], the wet-bulb temperature T wb [ 25.5°C ], the dew-point temperature T dp [ 23°C ], and the specific volume of the dry air v [ 0.89m 3 /kg ]. Indicate all the values determined on the chart There are two temperature information indication in every psychrometric chart. The first one is dry bulb temperature, which represents by the vertical line. When moving left to right, the dry bulb temperature is increasing. The other temperature indication is the wet-bulb temperature Every psychrometric chart includes Vertical lines that represent the dry bulb temperatures, Diagonals line represents wet bulb temperature Curved lines represent relative humidity Every psychrometric chart also includes wet bulb temperatures. These lines are indicated at diagonals, and like dry bulb temperatures they increase from left to right. Wet bulb temperature lines on a psychrometric chart

Read Dry Bulb, Wet Bulb Temperature on Psychrometric Char

On the psychrometric chart, the wet-bulb temperature lines slope upward to the left. The psychrometric sketch in Figure 4 shows the wet-bulb temperature of a moist air mixture when the dry-bulb temperature is 34°F and the relative humidity is 70%. Figure 4. Wet bulb line for 34°F dry bulb temperature and 70% relative humidity Psychrometric chart description O Vertical lines are dry-bulb temperature O Horizontal lines are humidity ratio (right axis) or dew point temp (left axis) O Slanted lines are wet-bulb temp and enthalpy O Specific volume are the other slanted lines 31 Only one point on the psychrometric chart represents air with both of these conditions. This point is located where the vertical 95°F dry-bulb (DB) and diagonal 78°F wet-bulb (WB) temperature lines intersect

When lines are drawn on the chart indicating changes in psychrometric conditions, they are called process lines. With the exception of relative humidity, all lines are straight. Wet-bulb lines and enthalpy (total heat) lines are not exactly the same so care must be taken to follow the correct line Normally lines of constant wet bulb temperature are shown on the psychrometric chart. The difference between actual enthalpy and the enthalpy obtained by following constant wet-bulb temperature is equal to (w2-w1)hf

Dry-Bulb Temperature - Tdb - can be measured by using a normal thermometer. With Dry-Bulb Temperature the sensible heat content in the air can be determined along the bottom axis of the psychrometric chart. The vertical lines extending upward from this axis are constant-temperature lines. Wet-Bulb Temperature - Tw Dry Bulb Temperature (DBT): Dry Bulb Temperature is the temperature determined by an ordinary thermometer. It is plotted on the X-axis of the Psychrometric Chart. Wet Bulb Temperature (WBT): Wet Bulb Temperature is the temperature registered by a thermometer whose bulb is covered by a wet cloth & is exposed to moving air. Dew Point Temperature. Wet Bulb Temperature: the lines that slant down from left to right The most important principal of a psychrometric chart is that if you know any two values of the air conditions, you can determine all other parameters. For example, the weather person says that the current air conditions are 75ºF and 60% relative humidity

Knowing both the dry-bulb temperature DBT and wet-bulb temperature WBTone can determine the relative humidity RH from the psychrometric chart appropriate to the air pressure. The term dry-bulb is customarily added to temperature to distinguish it from wet-bulb and dewpoint temperature What are the air Properties indicated in a psychrometric chart? Seven properties of atmospheric air are shown on the psychrometric chart. These properties are: dry bulb temperature, wet bulb temperature, dew point, humidity ratio, relative humidity, specific volume, and specific enthalpy Adiabatic saturation process follows the constant enthalpy line on the chart. The intersection between constant enthalpy line and the curve where the relative humidity equal to 100%, the temperature is the dew-point temperature. Spraying water at wet-bulb temperature represents by a vertical line on the chart

bulb temperature line and the 35 percent relative humidity line (which is not shown on the chart, but is midway between the 30 and 40 percent lines). Since evaporative cooling is the same process that determines wet bulb temperature, follow the wet bulb temperature line upward and to the left until the wet bulb temperature scale is intersected Alternate ISBN: 9780077359973, 9780077359980. Alternate ISBN: 9780077359973, 9780077359980. Thermodynamics (7th Edition) Edit edition Solutions for Chapter 14 Problem 36P: How do constant-enthalpy and constant-wet-bulb-temperature lines compare on the psychrometric chart? Dry bulb temperature-is the temperature of the air as measured by an ordinary thermometer (represented by vertical line on chart) 2. Wet bulb temperature-is the temperature of the air as measured by an ordinary thermometer whose glass bulb is covered by a wet cloth or gauze (represented by oblique lines at small angle) 3 Mechanical Engineering questions and answers. On a psychrometric chart, lines of constant wet-bulb temperature are approximately lines of constant mixture enthalpy per unit mass of dry air. True O False. Question: On a psychrometric chart, lines of constant wet-bulb temperature are approximately lines of constant mixture enthalpy per unit mass.

The lines shown below in Figure Two, are also referred to as constant temperature lines, and they are identified as Wet Bulb Lines. Figure Two These lines run down from the temperature scale on the curved section of the chart at an angle of approximately 30-degrees off of horizontal Jul 14,2021 - On Psychrometric chart, the constant wet bulb temperature lines coincide witha)constant relative humidity linesb)constant enthalpy linesc)constant dew point temperature linesd)constant volume lineCorrect answer is option 'B'. Can you explain this answer? | EduRev Mechanical Engineering Question is disucussed on EduRev Study Group by 1867 Mechanical Engineering Students Q10. On psychrometric chart, wet bulb temperature lines are a. horizontal with uniformly spaced b. horizontal with non-uniformly spaced c. inclined with uniformly spaced d. inclined with non-uniformly spaced View Answer / Hide Answe The Psychrometric Chart notes Dry-bulb temperatures are read from an ordinary thermometer that has a dry bulb. Wet-bulb temperatures are read from a thermometer whose bulb is covered by a wet wick. The difference between the wet-bulb temperature and the dry-bulb temperature is caused by the cooling effect produced by the evaporatio

1. On the Psychrometric chart, the dry-bulb temperature is the horizontal axis of the chart. ! Lines of constant wet bulb temperatures run diagonally from the upper left to the lower right in the Psychrometric chart. ! The vertical axis represents humidity ratio, the moisture content of the air mixture. I
2. Question is ⇒ The horizontal and non-uniformly spaced lines on a psychrometric chart indicates., Options are ⇒ (A) dry bulb temperature, (B) wet bulb temperature, (C) dew point temperature, (D) specific humidity, (E) , Leave your comments or Download question paper
3. The wet-bulb temperature is plotted on a psychrometric chart on the: Choose one answer. a. Right vertical axis b. Left vertical axis c. Lines which originate at the saturation line and slope downward to the right d. Horizontal axis on the bottom of the chart e. Relative humidity lines

Lines of constant wet bulb temperatures run diagonally from the upper left to the lower right in the Psychrometric chart. Dew Point Temperature - T dp The Dew Point is the temperature where water vapor starts to condense out of the air (the temperature at which air becomes completely saturated) Another point on the 70°F wet bulb line may be determined in a similar way. At 92°F dry bulb, a 22° F (92 - 70) wet bulb depression gives a relative humidity of 33%. This point is labeled C, and it is noted that points A, B, and C lie on a straight line ie the 70°F wet bulb line. Other wet-bulb lines can be plotted similarly The leaving air has a temperature of 22ºC without change in its moisture contents. Determine the; Question: a) Prove that the enthalpy of the humid air remains constant along a wet bulb temperature line on the psychrometric chart. b) The atmospheric air at 15ºC dry bulb temperature and 80% relative humidity is supplied to the heating chamber. Use the psychrometric chart to determine the specific humidity ω [18 gm-moisture/kg-air], the enthalpy h [78 kJ/kg-air], the wet-bulb temperature T wb [25.5°C], the dew-point temperature T dp [23°C], and the specific volume of the dry air v [0.89m 3 /kg]. Indicate all the values determined on the chart Wet bulb is very closely related to enthalpy, or the total heat in the air (dry bulb and wet bulb). In a psychrometric chart, the wet bulb lines are nearly parallel the enthalpy scale values. Return wet bulb temperature is mandatory for accurately charging a cooling system that incorporates a fixed restrictor metering device

In the Psychrometric chart, Dry-bulb temperature is indicated on the X-axis, and all vertical lines in the chart represent constant temperature lines. It is denoted as t d , t db , Tdb or DBT etc. Dry-bulb temperature can be measured using a normal thermometer freely exposed to the air but shielded from radiation and moisture psychrometric charts Dry-Bulb Temperature • Dry-bulb temperature is the temperature of an air sample, as determined by an ordinary thermometer, the thermometer bulb being dry. It is typically the abscissa or horizontal axis of the graph. The SI unit for temperature is Celsius, the other unit is Fahrenheit. Wet-Bulb Temperature 70°F Dry Bulb. Fig. 34-11 Wet-Bulb Temperature Lines. 70°F Dry Bulb. Fig. 34-11 Wet-Bulb Temperature Lines. Fig. 34-9 Dewpoint Temperature Scale. Fig. 34-9 Dewpoint Temperature Scale. cally on the left, but sometimes on both sides, of the chart. Typically, the scale ranges from about 5 to 60 Btu/lbm (12 to 140 kJ/kg) This will take us to a point B on the wet bulb temperature line. Point B represents the conditions of the air leaving the evaporative cooler. CONDITIONS OF AIR LEAVING EVAPORATIVE COOLER (POINT B ON CHART) Dry bulb temperature = 21° C Wet bulb temperature = 20° C Relative humidity = + 90 % Low sensible heat (energy) High latent heat (energy

4. Draw the schematic of a psychrometric chart 5. Discuss the straight-line law and its usefulness in psychrometry 6. Explain the concepts of adiabatic saturation and thermodynamic wet bulb temperature 7. Differentiate between thermodynamic WBT and WBT as measured by a wet bulb thermometer 8 The dry bulb temperature runs along the x-axis and is indicated by evenly spaced vertical lines.It is represented by vertical lines as shown below in the psychrometric chart. Wet Bulb Temperature: In simple language, the wet bulb temperature is measured with a wet bulb i.e. a bulb which is wrapped in a wet cloth

Psychrometric Chart Use - Penn State Extensio

You can also read the web-bulb temperature from a Psychrometric chart.From the current point, draw a line parallel to the lines of constant wet-bulb temperature, until you reach the 100% relative humidity line, and then read the temperature.This is illustrates by the green line on the chart below Create. Sling psychrometer is used to measure which of the following temperature (s): A;Both dry bulb and wet bulb. B:wet bulb. C:Dry bulb. A;Both dry bulb and wet bulb. As the amount of moisture suspended in the air _____, the wet-bulb depression increases. A:decreases. B:increases 13. What is the range of DBT on the psychrometric chart usually used? a) 0 to 30°C b) 0 to 45°C c) -6 to 45°C d) -2 to 45°C. Answer: c Clarification: Generally, the temperature range of dry bulb temperature lines on the psychrometric chart is from -6 to 45°C. These lines are drawn with a difference of every 5°C of DBT. 14 13. What is the range of DBT on the psychrometric chart usually used? a) 0 to 30°C b) 0 to 45°C c) -6 to 45°C d) -2 to 45°C Answer: c Clarification: Generally, the temperature range of dry bulb temperature lines on the psychrometric chart is from -6 to 45°C. These lines are drawn with a difference of every 5°C of DBT. 14 Temperatures - Dry Bulb/Web Bulb/Dew Poin

Psychrometric Chart A. Trace the line of 40% relative humidity B. Trace the line of 22 C wet bulb temperature. Psychrometric Chart A. Trace the line of Humid Volume = 0.85 m3/kg Dry Air B. Trace the line of sat'denthalpy = 65 kJ/kg Dry Air This is the enthalpy of the (air + moisture) divided b Wet bulb temperature on psychrometric chart is represented by lines that slant diagonally from the upper right of the chart (along the line of saturation) down to the lower left of the chart. These follows lines of constant enthalpy but values are read off at the upper, curved, saturation temperature boundary. The unit of measure used fo  Psychrometrics, Part 2 - The Quantities in the Chart

pressure at the same temperature. This can be expressed in the equation: RH = P 1 /P s Where: P 1 = Partial pressure of the water vapor at the dew point temperature of the mixture of dry air and water vapor, P s = Saturation pressure of the water vapor corresponding to the dry bulb temperature On the psychrometric chart, the wet-bulb lines are very nearly parallel to the enthalpy lines. If we know both the wet bulb and dry bulb temperature of the air, its absolute moisture content can be found easily by using the chart. The concept of wet-bulb is useful because it is a relatively simple and inexpensive way to measure air moisture

Psychrometric Properties in EES 8 Given: Moist air at 1 atm, 85°F, 40% relative humidity Find: The following psychrometric properties of the mixture using EES (a) humidity ratio (b) specific enthalpy (c) specific volume (d) wet bulb temperature (e) dew point temperature Using the enthalpy value of 19.8 and the moisture content value of 0.00648, plot the mixed air conditions, Point C, on Chart No. 1, Figure 9, by drawing a horizontal line across the chart at the 0.00648 moisture content level and a diagonal line parallel to the enthalpy lines starting at the 19.8 Btu per pound of dry air enthalpy point

For most applications the only information available is the dry bulb and relative humidity or dry bulb and wet bulb temperatures. The psychrometric chart is used to plot these two values by finding their intersection and then following the horizontal line to the right to determine the moisture content in grains per pound Find the intersection of the two known properties, dry-bulb and wet-bulb temperatures, on the psychrometric chart, Figure 1. The dry-bulb temperature is located along the bottom horizontal axis. Find the line for 78 o F, which runs vertically through the chart. Wet-bulb temperature is located along diagonal dotted lines leading to scale. The wet bulb temperature of the entering air as read from the psychrometric chart is tw1=26.1 ºC Final dry bulb temperature Let td2 = final dry bulb temperature of the air leaving the air washer We know that humidifying efficiency of an air washer (ηH), t −t 35 − t d 2 0.85 = d 1 d 2 = t d 1 − t d 3 35 − 26.1 ∴ td2 = 35-0.85×8.9=27. iii. Extend the vertical line which is the dry bulb temperature form 78°F and the diagonal wet bulb line form 65°F and get the point of intersection iv. Find out the values of various parameters at this point. 7 8 Psychrometric Properties 1. Dry bulb temperature 2. Wet bulb temperature 3. Dew point temperature 4. Relative humidity 5 PSYCHROMETRIC CHART CARRIER A dry bulb air temperature thermometer reads degrees Fahrenheit and a wet bulb thermometer lsychrometric 68 degrees Fahrenheit. Also known as air temperature, the reading of psychrimetric unwetted bulb in a thermometer. The dew point is the temperature below which the water vapor in air condenses into liquid water at.

Wet Bulb Temperature. Wet bulb temperature is the temperature a volume of air would be if it was cooled to saturation (100% relative humidity). Looking at this from the perspective of the psychrometric chart, if we were outside on a day with a 110°F temperature and no humidity, we could follow the wet bulb temperature line to the wet bulb axis. The wet-bulb temperature is approximately 75.4°F. All other properties can be read directly. FIGURE 6. Cursor over dry-bulb temperature lines up with correct wet-bulb temperature GIVEN DRY-BULB TEMPERATURE AND RELATIVE HUMIDITY Assume that you have a given dry-bulb temperature of 80°F, and a given relative humidity of 50%. First, turn the mai

How do I read a Psychrometric Chart. Relative Humidity can be calculated with a wet bulb thermometer and a dry bulb thermometer, using a psychrometric chart as below. Wet-bulb temperature is measured using a thermometer, with the glass bulb or sensor tip wrapped in a wick, which is kept wet ANSWER: unsaturated air. Explanation: No explanation is available for this question! 5) At 100% relative humidity, the wet bulb temperature is. a. lower than the dew point temperature. b. higher than the dew point temperature. c. equal to the dew point temperature. d. none of the above. Answer Explanation The straight-line joining 1 and 2 represents the path of the air as it passes through the adiabatic saturator. Normally lines of constant wet bulb temperature are shown on the psychrometric chart. The difference between actual enthalpy and the enthalpy obtained by following constant wet-bulb temperature is equal to (w2-w1)hf. Fig 1 Wet-bulb temperature (WBT) The thermodynamic wet-bulb temperature is a thermodynamic property of a mixture of air and water vapor. Knowing both the dry-bulb temperature (DBT) and wet-bulb temperature (WBT), one can determine the relative humidity (RH) from the psychrometric chart appropriate to the air pressure

The dew point temperature lines on psychrometric charts

This temperature can then be read from the thermometer. Air at 20C, rh70% (point 1) will have a wet bulb temperature of 14C (point 3). A sling thermometer is a thermometer which is mounted on a handle so it can be swung round in the air. This rapid air movement over the wet bulb means this will reach the wet bulb temperature more quickly Here, boundaries of the psychrometric chart are comprised of dry-bulb temperature scale on the horizontal axis ( abscissa ), and humidity ratio (moisture content)( ordinate ) scale on the vertical axis. where as an upper curved boundary represents saturated air or 100 percent moisture holding capacity

The curved lines on a psychrometric chart indicate

same design conditions of 90°F Dry Bulb, 75°F Wet Bulb, and 2000 cfm of outside air. On the following psychrometric charts, different color lines represent different air properties: Blue Line = Cooling Process Yellow Line = EAT Dry Bulb Temperature Red Line = EAT Wet Bulb Temperature Green Line = EAT Enthalpy Black Line = LAT Dry Bulb Temperature turned on, the air temperature will be cooled to the wet bulb temperature. On the psychrometric chart, the wet-bulb temperature lines slope upward to the left. The psychrometric sketch in Figure 4 shows the wet-bulb temperature of a moist air mixture when the dry-bulb temperature is 34°F and the relative humidity is 70% ; A T HE CHART Figure 1 shows a typical psychrometric chart. Dry Bulb temperatures are shown on the chart as vertical lines. The horizontal lines represent Dew Point temperatures. Lines representing Wet Bulb temperatures are the straight diagonal lines sloping downward from left to right. The curve forming the top edge of the chart is called th The curved lines on a psychrometric chart indicates. a) Dry bulb temperature. b) Wet bulb temperature. c) Dew point temperature. d) Relative humidity. Refrigeration & Air-Conditioning Practice Set-3. Related. Super Smart VPN Safe and Secure. Ads by Google. Civil Engineering MCQs

Calculating the Dew-Point and Wet-Bulb Temperature of Ai

Dry bulb temperature lines shown on the Psychrometric Chart Temperature: Wet Bulb The wet bulb temperature (WBT) is a temperature associated with the moisture content of the air. Wet bulb temperature is taken by surrounding the thermometer with a wet wick and measuring the reading as the water evaporates. Because of the evaporativ the higher its dew point temperature. When dry-bulb and wet-bulb temperatures of the air are known, the dew point temperature can be plotted on the psychrometric chart (Fig. 4). Dry-bulb temperature: The temperature read directly on an ordinary thermometer. Isothermal process: A process in which there is no change of dry-bulb temperature Locate state point on the psychrometric chart at the intersection of 40°C dry-bulb temperature and 20°C thermodynamic wet-bulb temperature lines. Read humidity ratio W = 6.5 g (water)/kg (dry air). The enthalpy can be found by using two triangles to draw a line parallel to the nearest enthalp Vertical lines on psychrometric chart. describe the dry bulb temperature. Lines go up and down. dry bulb temperature. is the ambient temperature on the spaces being measured. measured in F. wet-bulb temperature on psychrometric chart. are lines slanting upward from the lower right hand corner to the upper left hand corner You can also read the web-bulb temperature from a Psychrometric chart. From the current point, draw a line parallel to the lines of constant wet-bulb temperature, until you reach the 100% relative humidity line, and then read the temperature

Free Online Interactive Psychrometric Chart. A convenient, precise and customizable psychrometric chart & calculator tool for HVAC engineers. Support IP and SI units calculations will assume the same design conditions of 90°F Dry Bulb, 75°F Wet Bulb, and 2000 cfm of outside air. On the following psychrometric charts, different color lines represent different air properties: Blue Line = Cooling/Heating Process Yellow Line = EAT Dry Bulb Temperature Red Line = EAT Wet Bulb Temperature Green Line = EAT Enthalp lines. 10. In the psychrometric chart, constant wet bulb temperature lines are the same as constant lines. 11. In the psychrometric chart, constant enthalpy lines are the same as constant lines. 12. A vertical line on the psychrometric chart corresponds to a constant line. 13 Here are the easy 8 step framework designed to demystify the psychrometric chart: Step 1:-. Locate the dry bulb temperature along the bottom axis and the associated vertical line for each temperature. This scale will be in degrees F or degrees C. Step 2 :-. Locate the 'humidity ratio' along the right vertical axis THE PSYCHROMETRIC CHART: at 60°C dry bulb temperature and 52°C wet bulb temperature. The drying rate of the lumber is 12.5 kg of water per hour. If outside air is at 27°C Therefore, length of line segment 1-3 is 0.21 times the length of line 1-2. 2 3 1 0.87 m3/kg d.a. 0.95 m3/kg d.a. 43.3°C 37.8°

Using the Psychrometric Chart Problem Statement The air in a oroom has a dry‐bulb temperature of 80 F and a wet‐bulb otemperature of 65 F. Assuming a pressure of 14.7 psia, use the ppysychrometricchart to determine: 1. The specific humidity. 2. The relative humidity. 3. The dew point temperature This on-line program calculates typical psychrometric state point properties. It will also provide a number of other thermodynamic properties not found on a typical psychrometric chart. To calculate properties, the user must enter either a site elevation (from which an average barometric pressure is calculated) or an actual barometric pressure The Dry bulb temperature refers to the ambient air temperature, which remains unaffected by air moisture, and this variable is shown as the horizontal axis of a psychrometric chart. Wet bulb temperature has essentially the reverse effect of this process, involving covering the bulb of the thermometer with a wet cloth before taking a temperature. With Dry-Bulb Temperature the sensible heat content in the air can be determined along the bottom axis of the psychrometric chart. The vertical lines extending upward from this axis are constant-temperature lines. Wet-Bulb Temperature - T wb. Wet-Bulb Temperature is associated with the moisture content of the air Psychrochart . A python 3 library to make psychrometric charts and overlay information on them.. It implements a useful collection of psychrometric equations for moisture and humid air calculations, and the generation of beautiful and high customizable psychrometric charts in SVG with matplotlib.. Psychrometric calculations to make the chart data are done with PsychroLib (summary paper in.      Wet-bulb temperature The vertical and uniformly spaced lines on a psychrometric chart indicate. Q9. The sensible heat factor is the ratio of: Q10. In a Psychrometric chart, horizontal lines represent constant. Q11. The wet bulb and dry bulb temperatures of an air sample will be equal when: 1. Air is fully saturated 2 Psychrometric charts are available in SI (metric) and IP (U.S./English) units. They are also available in low and high temperature ranges and for different pressures. (1) Determining relative humidity: The percent relative humidity can be located at the intersection of the horizontal dry bulb and diagonally down sloping wet bulb temperature lines Locate the uppermost curved line on the chart to find the saturation curve. This curve connects the X and Y axis, and marks the relationship between temperature and absolute humidity when the relative humidity is 100%. Along this line, note that the wet bulb temperature and the dew point are always equal to the dry bulb temperature In practice, the bar for this wet bulb temperature, which is measured by covering a Many of these countries are on the front lines. CNN, wet and dry bulb hygrometer, 410a wet bulb chart, psychrometric chart wet bulb temperature, psychrometric chart dry bulb wet bulb, psychrometric wet bulb temperature, psychrometric.